4-Month Scale Control Test a Real Success!
A four month evaluation of FlowMark has just been completed in Mexico. This customer has 18 evaporative condensers that suffer from heavy scaling (See left Picture). Two other physical treatment technologies have failed to help solve the problem.
These condensers have no conductivity control. Instead, the systems are drained and refilled once a week with fresh water. The water has calcium carbonate concentration starting at 200 PPM and cycling up to 900 PPM by the end of the week. The silica levels start at 65 PPM and cycle up to 280 PPM (about 4.3 cycles).
The FlowMark model Mark-III has kept the condenser tubes free of scale despite unorthodox conductivity control as seen in the right photo above. This system saves a lot of money in cleaning expense and repairs. Needless to say, the Customer is very pleased.
Over the past 3 years FlowMark has produced well over 100 Web Induction systems for Leachate scale control applications. Results on a wide variety of challenging applications have been very positive. In order to support the enormous Leachate Scale Control market, FlowMark is requesting our Authorized Representatives follow our new aggressive suggested retail pricing structure.
Trust the ORIGINAL FlowMark for your Leachate Scale Control needs.
How does 22 months of pipes with NO Calcium Scale sound? Download the Hinkley Center Report below for details.
A large New York State Manufacturer sees firsthand how well the Web Induction Pulsed Power Water Treatment System manufactured by FlowMark removes calcium carbonate from high conductivity water (about 1550 micro-siemens). FlowMark systems promotes the formation of calcium carbonate seed crystals in the treated water which fall out of solution in quiet areas of the cooling tower system instead of plating out as hard scale deposits inside the chiller or on the tower fill. In the photo above one can notice the large amounts of loose granulated calcium carbonate on the tower basin floor and the absence of any scale in the tower fill.
The loose granulated calcium carbonate is easily removed by manual cleaning.
A FlowMark Chemical-Free Water Treatment System was installed on the 300 ton steam
powered Absorption Chiller and cooling tower. In addition, a bag filtration and Creative Water
Solutions ProMoss filtration system was installed to maintain clean water in the cooling
system. This system eliminates hazardous chemical use for the cooling system. The biological
counts are consistently less than 500 CFU/ml, corrosion is controlled and the water in the
cooling tower is crystal clear.
In cooperation with Volusia County Schools HVAC Management, FlowMark Water Treatment of Daytona Beach, FL has successfully completed a 6 month paid trial to prove the validity of their Web Induction Pulsed Power and Advanced Oxidation Systems. All conventional chemical treatment was suspended during the trial period. The FlowMark chemical free system provided excellent scale and bacteria control while operating at high cycles of concentration to conserve water. Management was impressed and is not considering a chemical free water treatment bid for all schools.
Fjord Line of Denmark has purchased two FlowMark Web Induction Pulsed Power systems to
protect the potable water plumbing systems of two new ships.
The Web Induction systems are installed on the discharge piping o the bulk water tanks in
order to prevent calcium scale from forming throughout the ships extensive plumbing system.
Success was immediately apparent when the ships engineers realized that FlowMark was
preventing scale from forming on the quartz tubes of the ships Ultraviolet Disinfection System.
FlowMark is protecting hot water boilers. kitchen equipment, cabin fixtures. disinfection
systems and all piping from hard water scale.
In effort to save water and reduce their environmental footprint, the Plaza Resort & Spa in Daytona Beach, Fl. has changed the way they treat their cooling tower water. Waterhouse Corporation of Deltona, Fl. was contracted to replace the existing chemical water treatment program on 5 cooling towers with chemical free systems manufactured by Flow-Mark Water Treatment of Daytona Beach, Fl.
The FlowMark Pulsed Power Systems allow the cooling towers to operate at higher cycles of concentration which saves an enormous amount of water that was previously being wasted. FlowMark’s Advanced Oxidation Process provides the biological control, killing bacteria including Legionella, viruses, fungi and mold. The cooling tower water is now crystal clear and safe.