FlowMark Disinfection Systems (DS) have been developed to enhance biological control of our Pulse Power Water Treatment product line. Dozens of cooling towers are maintaining excellent biological control using only our Pulsed Power System as it promotes calcification of microbes which limit their ability to metabolize nutrients and dispose of waste. Typical Bacteria Plate Counts (HPC) average 500 CFU/ml or less with our Mark series products alone. In cases where the mineral content of the make-up water is too low to promote calcification of microbes or when persistent algae growth is a problem we now have the product to fill the gap with FlowMark DS Systems.
In October 2013 a FlowMark model Mark-III was installed on the 6” diameter PVC riser of a 300 ton evaporative condenser at a medical building in Lake Marry Florida. All chemical treatment was discontinued.
Over the course of 12 months the conductivity bleed set point was gradually increased to attain maximum water savings. Cycles of concentration by chlorides were increased from 4.1 to 14.5 with no new scale forming.
In October 2013 a side by side study comparing FlowMark Electronic Water Treatment to conventional chemical water treatment began at a prominent insurance company in New York. Towers 1 & 2 remained on chemical treatment and a FlowMark Electronic Water Treatment System model Mark-III was installed on the 6” steel condenser water pipe feeding towers 3 & 4. All chemical treatments to towers 3 & 4 were discontinued. This document details findings following the 9 month comparison.
A test was conducted to see what affect FlowMark Electronic DAF Water Treatment would have assisting blood removal from wastewater.
Influent to the DAF was pumped from a batch equalizaon tank that was connuously mixing.